Requirements of Bed material,Charcoal & Diesel. Bed material Maximum Particle size Bulk density Chemical composition MM TO The start up of fluidised bed combustion boilers has always been a subject of the most process of raising bed temperature above °C. In the process of. boilers/heaters is the concept of Fluidised Bed Combustion (FBC). A descriptive feature for Start up/ Firing Procedure for AFBC boiler/heater bed. Initially.
|Published (Last):||3 February 2007|
|PDF File Size:||4.77 Mb|
|ePub File Size:||20.32 Mb|
|Price:||Free* [*Free Regsitration Required]|
After stabilisation of bed temperatures stop the burners and Lighht pumps. Keep the PA lines clear and take trial run of feeder of first compartment. CFBC boiler operation procedure? Cethar Afbc Boiler Manual – dire searching for a ebook Cethar afbc boiler manual in Once fludisation study is completed boiler is ready for light up.
Set the air flow to MM of wc P. All interlocks to be cross checked.
THERMAL POWER PLANT A-Z: boiler light up detailed
Boiler Installation – Afbc Documents. Fuel feeders and controllers. Afbc Boiler Operation Manual – boiler bokler procedure 1 seminar afbc boiler operation procedure,Ask Latest information,Abstract,Report,Presentation free download cfbc Documents.
Ensure all equipment trial to be taken. Turn off the oil burners and remove from furnace. Afbc Boiler Operation Manual – boiler operation manual at Ensure the deaerator water level as normal. C and stable the boiler. Close the bed superheater drains. Shiatsu Massage Manual Afbc boiler boiler, The Light up all the four burners. Valves before and after feed control valve in feed line. Ensure all personel were cleared. Check instrument air pressure is available at the required pressure 7 to 7.
Bed super heater drains. Afbc Boiler Operation Manual – snowman-ro. Bed material to be filled and level of defluidised bed should be MM of WC. Initally the top bed temperature will raise and at the time of mixing temperature drops and bottom temperature raises at the time of mixing.
Check the following valves in boiler are in closed condition. Boiler Manual For Cfbc – boiler operation procedure?
Start the LD oil pump and maintain the oil pressure between 6. Check the following equipments procecure adequate lubrication. Bed material Maximum Particle size Bulk density Chemical composition: Afbc Boiler Operation Manual – ante-annum.
AFBC ( Atmospheric Fluidized Bed Combustion ) BOILER COLD START UP PROCEDURE – ASKPOWERPLANT
Published on Oct View 3. Cfbc Boiler s,ebooks and documents of cfbc boiler operation manual thermax – afbc boilers, When the bed temperatures reaches Deg C start the drag chain coal feeder. Cfbc boiler operation procedure? Boiler light up procedure A fixed quantity of dry charcoal Lightt i. Check the following valves are kept in open condition. Start up boile valve. Check for dry fuel MM is available in bunker and gates below bunker are open and fuel is available at feeder inlet.
Afbc Boiler Light Up Procedure
Feed pump and drives. The pressure drop across bed is obtained for various air flow. Ensure feed water flow through economiser at the time of light up to avoid steaming of economiser. Inspect the boiler before start and check the following 1. Add gas plenum pressure P2 Furnace draught to P1.
A fixed quantity of diesel wetted Charcoal 40 Kgs is spread uniformly over the compartment. Start the FD fan and maintain bed pressure mmwc.
Inspect the boiler before start and check Manual on Boiler Tube Fluidized bed combustion – wikipedia, the free encyclopedia Fluidized bed combustion FBC is a combustion technology used to burn solid fuels. Drum and main line vent. C and start the ash handling system.
Ensure all foreign materials are removed from furnance and pressure parts. Measure air box pressure P1 MM of wc 3.